ELEXIUM electrical box
ELEXIUM electrical box with filtration command without trip
Timeclock for programming,
Easy to use,
In respect of electrical norms C15-100 the power supply of an electrical box for filtration purposes should be fitted with a 30mA differential switch.
Indication of amperage for the calibration of trip switches
|Filtration pump capacity (kW / HP)||Trip switch calibration of trip switches||Amperage|
|0,25 / 0,33||1,6 / 2,5||2,2A|
|0,37 / 0,50||2,5 / 4,0||3,12 A|
|0,55 / 0,75||4 / 6,3||4,76 A|
|0,75 / 1||4 / 6,3||6,01 A|
|1,1 / 1,5||6 / 10||7,60 A|
|1,5 / 2||10 / 6||10,40 A|
Pre-installed trip switches used are double pole.
|Filtration pump capacity (kW / CV)||Trip switch calibration of trip switches||Amperage|
|0,25 / 0,33||1,0 / 1,6||0,9 A|
|0,37 / 0,50||1,0 / 1,6||1,2 A|
|0,55 / 0,75||1,6 / 2,5||1,60 A|
|0,75 / 1||1,6 / 2,5||2 A|
|1,1 / 1,5||2,5 / 4||2,60 A|
|1,5 / 2||2,5 / 4||3,50 A|
|2,2 / 3||4 / 6,3||5 A|
|3 / 4||6 / 10||6,60 A|
Pre-installed trip switches used are three pole.
Description of the ELEXIUM electrical box
2. Dovetail wall fixation enables drilling, lining up and fixation without marking.
3. Ergonomic border hand grip
4. Opening and closing using 2 1/4 turn screws.
5. A cable stopper avoids all risk of tearing out the cable when powered.
6. Cable crossings positioned on raised flat base giving direct access to terminal connections (for cable gland ISOM20 & M25).
The electrical box for filtration only gives the possibility of programming the filtration time by means of the integrated timeclock. A 3-position switch gives the choice of filter stop/on/programmed start and stop.
This model lets you program filtration time by means of the integrated timeclock and a transformer with on/off switch commands your lighting projectors.
The command box must be placed in an easy to reach area, that permits correct operation (C15-100 et 771,558), correctly aired, easy access with no obstacles placed in front of the box. The box should be placed between 1m and 1,80m above ground level. Height is limited to 1,30m, taking into account wheelchair access (C15-100 et 771,558). Prohibited in volumes 0,1 and 2. (C15-100 and 702,51). The box should be installed at a minimum distance of 3,50m from the pool and by preference, in the technical shelter.
The cable sections must be dimensioned to support the amperage of the box. The cable length must not cause a voltage drop greater than 5% of the original power source generated (C15-100 section 525). Table 1 shows the values for a copper cable, depending on the dimension of its section, power source, maximum amperage and maximum length for the indicated amperage. The ELV (12V) of the pool : Table 2 shows values for a copper cable section, depending on the power of the transformer and the cable section. The guidelines concerning the ELV cable section, circuit breaker and trip switch dimensions are given in the guide UTE C15-559. In the case of voltage drop, the norm cannot be applied for residential pools as the lifespan of the material will be diminished.
|Section||Maximum amperage||Single phase 220V Maximum length||Three-phase 380V Length|
Electrical installation conditions
|Volume||ELV elements used||Appliance used|
|1||For small pools, a plug socket fitted with a differential circuit breaker superior to 30mA is admitted to more than 1,25m from the pool and lesser than 0,3m from ground level||ELV|
|2||ELV separating transformer (installed out of volumes 0, 1, 2). The power source should be protected with a differential greater than 30mA.||ELV separating transformer (installed out of volumes 0, 1, 2). The power source should be protected with a differential greater than 30mA. Class II lighting.|
Installation schema for ELEXIUM electrical box
Price incl. VAT
Ask for a free quote elexium electrical box
Other product : ELEXIUM electrical box
Starting from 182 eur Including VAT.
Please fill in this form carefully. Our commercial service will handle your request promptly.
UK freephone hotline
Monday Friday 9.00 19.00, Saturday 10.00 18.00